Commercial Fire Communication Solutions
The reliability and flexibility of cellular alarm communication are increasingly making it the first communication channel choice for new installations. In existing systems, many users are replacing their landlines with cellular service for fire alarm control panels (FACP).
The XR150FC and XR550FC Fire Series Control Panels are UL 864 for commercial fire installations. These panels are available individually with the keypad built in the cabinet or without a keypad. They are also available as panel packages with or without the fire annunciator keypad built in. Network and two-line dialer options are available, and dealers can upgrade control panels to add cellular communications for fire installations. The 263C or 263H Digital Cellular Communicator is an easy-to-install module that creates a direct, wireless communications path to any DMP central station receiver.
The new FC Series Control Panels are listed for Central Station System, Remote Station System, Proprietary and Local. This includes service types: Automatic Fire Alarm, Manual Fire Alarm, Sprinkler Supervisory and Water Flow Alarm.
Slave Communication for Fire Applications
The XR150 and XR550 has added versatility with UL864 certification as a slave communicator that transmits via network or cellular communications in commercial fire installations and is compatible with any FACP.
Dealers can upgrade existing XR150 and XR550 panels to add cellular communications by adding the 263H/381-2 and 263C/381-2 Cellular Communicators, an easy-to-install expansion card that creates a direct, wireless communications path once activated with SecureCom Wireless to any DMP central station receiver. Dealers can also order panels with network communications onboard. Both options will allow the DMP panel to be used as a slave communicator for an existing FACP.
In addition to standard hardwire slave communication installations that connect inputs to the XR150/XR550 control panel, DMP panel slave communicators can also be installed using the 1100X Wireless Receiver or 1100XH High Power Wireless Receiver with 1103 Wireless Transmitters to communicate the FACP status. Refer to diagrams 1.10- 1.12 in the Compliance Listing Guide for Panel Slave Communication for FACP.
When equipped with the cellular communicators, the panels also offer the convenience of DMP's Virtual Keypad app, supervised cellular communication and real-time status information for integration with third-party control and automation systems. Mobile applications can immediately text or alert the building manager, maintenance supervisor or on-site safety/security director upon alarm or troubles.
Commercial Wireless Fire Devices
The list of DMP wireless devices that have earned the UL Commercial Fire Listing include:
1103 Universal Transmitter: A two-input transmitter with wall and case tamper, typically used in commercial burglary door or window applications.
1100R Wireless Repeater: Extends the communication range of DMP receivers, enabling physically larger, more reliable wireless security systems.
1100XH High Power Wireless Receiver: Provides additional transmit and receive amplification for improved performance at greater distance or in harsh building environments.
Commercial Smoke Detectors: The 1164 smoke detector includes synchronized sounders so when more than one 1164 is installed on a system, the alarm cadence will synchronize. Any fire zone tripped on the panel will cause the sounders to initiate. The 1164 also includes a tamper switch that sends a trouble signal when the detector is removed from the mounting base. Up to 572 units can be installed on one system. The 1164NS with no sounder is also available for applications with existing sounder/notification devices.